TEE offers a complete heater bank (electric duct heater) package for the HVAC industry.
Thermal Electric uses high quality materials in all units, including Stainless Steel finned heating elements to ensure long-lasting and efficient use. Some companies will supply electric duct heaters with a mild steel painted surface finish which continuously bakes or burns over a period of time, releasing fumes into the duct. These fumes are known to cause Sick Building Syndrome (SBS) which affects all individuals within the building and can result in unwanted illness and possible liability.
Sick Building Syndrome is often caused by a HVAC system that is re-circulating polluted air.
Our SBS white paper can explain this in more detail.
Thermal can design and manufacture one off EDH units or hundreds of units, for projects both large and small,
view our Experience List for more information on the projects we've worked on.
Finned Air Heater Banks
Air Heater Banks for Duct Applications
Complete air heater banks incorporating the choice of elements are designed and built to meet the requirements of individual air conditioning installations. Once we have been provided with full details of the job, the most economic arrangement of elements, banks, etc, will be selected to comply with requirements. Terminal boxes are custom made to suit your duct size. Heaters are wired in the number of steps required to a terminal block inside, therefore enabling your electrician to connect up power supply easily.
Duct Heater Handing Side
To improve the efficiency of TEE Electric Duct Heaters, Thermal designs all units with a specified handing side based on the customers requirements and site limitations. By selecting a handing side relevant to the particular duct installation, on-site servicing is made much easier by facing the unit in a more easily accessible direction. Determining the best handing side for an electric duct heater also optimises the performance of the unit by allowing for much more thorough over temperature monitoring based on the position of the unit within the duct. The handing side is based on the ductwork that the unit is being installed into when looking down the duct with the airflow coming towards you. The handing is then specified as either Left hand side or Right hand side.
The picture to the right shows an EDH with a Left Handing configuration.
Job data required for finned or unfinned heater banks
- Nominate the element to be fitted or standard specified, ie, AS1668 Part 1 or AS3102
- Size of duct and entry side for bank.
- Handing direction - Left or Right.
- Total kilowatts required.
- Number of control steps needed and whether wiring is single or 3 phase.
- Details of controls required to be fitted to the units.
Air Heater Banks for Package Units
Package unit heaters comprise of elements mounted in a steel frame with removable terminal cover for easy connection of power supply by electrician. Job data required as above. (Disregard item 2 and instead state the size or brand model of air conditioning unit requiring the heater.)
Individual air heater elements
Individual finned heater elements are also available from our wide range of standard units, or custom designed to suit your specific needs.
Elements are available in straight, U, W or Triple U-forms and rated at 240V with Stainless Steel sheath and fin.
If you would like more information on our finned heater range, download our specs sheets.
Controls for the air conditioning industry
In accordance with AS1668 Part 1, temperature controllers and air pressure switches are required to eliminate overheating and possible premature failure of duct heaters.
Over Temperature controllers:
An over temperature controller is a thermally operated switch, designed to provide protection when it's capillary tube is heated above a preset cut out temperature. This could be caused by an accidental cutting of the air flow. Over temperature controllers come in both manual and automatic reset. The units are fail safe, if capillary is ruptured, the contacts open automatically.
Standard 2-hole mounting
Standard capillary length of 600mm
Standard lead length of 300mm
Other controls and accessories such as Air Pressure Switches and PENN type thermostats are also available
Evapodry Condensate Tray
Thermals Evapodry tray can solve the problem of unwanted condensate by evaporating it from underneath the split systems compressor. The tray simply slides under the compressor and is plugged in.
The probe senses condensate that has accumulated in the tray and energises the heating element. When the probe senses the liquid has evaporated, the heating element is turned off.
The standard tray size is 400 x 400 x 55mm deep. Or a tray can be designed to suit your needs.
The standard tray uses a 240V 1000W heating element.
This tray conforms to health and safety standards in accordance with Plumbing Industry Commission - Section 7 Part E.
Thermal's HVAC Experience
TEE have supplied electric duct heater units to a wide range of projects throughout Australia and overseas, including Singapore and Papua New Guinea.
See below for a list of some of the projects we have supplied:
- Northern Territory Prison Secure Facility
- Gold Coast University Hospital
- Brisbane Supreme and District Courts
- Royal North Shore Hospital
- Robina Hospital
- Carrara Stadium
- Orange Hospital
- La Trobe Bioscience Lab
- Big W Mirrabooka Square
- 550 Bourke St - a 5 Star Green Star rated building
- Cairns Base Hospital
- Glen Waverley Police Academy
- Geelong Hospital
- Cadia Valley Mine
- RMC Majura
- Mackay Base Hospital
- Kumul Topside Rejuvenation
- Brisbane Convention & Exhibition Centre
- Prince Charles Hospital
- PNG LNG
- and many more...
View the terms of our product warranty.